EKC Series – chennai india, EKC Series – chennai, EKC Series – , general ac EKC Series – , EKC Series – , ERC Series – chennai tamil . RI8NB R INSTRUCTIONS. EKC D (B). R Type: Pt Instructions RI8NB © Danfoss 05/ EKC D. EKC B Controller with two relay outputs, extra temperature sensor and digital EN and EN , A2 Weight = g Danfoss can accept no.
|Published (Last):||21 September 2013|
|PDF File Size:||1.88 Mb|
|ePub File Size:||6.64 Mb|
|Price:||Free* [*Free Regsitration Required]|
Regulation is carried out when the input is short-circuited, and regulation is stopped when the input is put in pos.
There is no alarm delay. If D10 has been set at 0 or 2 the S5 input can be used as product sensor or condenser sensor. DI input is open S Thermostatic Expansion Valves flow direction: Pyskowicka 24, Zabrze in the scope necessary for drawing up and sending a reply to my message, which was sent to the administrator by the above contact form.
Control Danfoss EKC 102D 084B8506
Copying key not correctly mounted 5: Roof mounted industrial Electrical defrosting air cooler low temperature DJ series for cold room. We will reply as soon as possible.
We also inform you that: Push briefly 1s the upper button. After two seconds you can move back into the mennu again and check whether the copying was satisfactory.
When the temperature passes a set allowed variation the defrost will be started. Hermetic Compressors c02 min. The function delays the interval time d03 by danofss set number of minutes, but it only does it once, and this at the very first defrost taking place when voltage is connected to the controller. The abovementioned does not influence compliance with the right to process data, which was performed on 012 basis of the consent expressed by you, before you withdrew it.
After two seconds you can move into the menu again and check whether the copying was satisfactory. Select your own number.
HVAC Danfoss Electronic Temperature Controller type Danfoss EKC D B for Freezer
The Danfoss controller is used for applications where temperature is critical. Here you can set the time delay. When the controller demands refrigeration it will first cut in the compressor with the shortest operating time.
The relay is cut out during normal operation and cuts in in alarm situations and when the controller is dead de-energised Refrigeration 2. Here are the messages that may appear: It’s a community-based project which helps to repair anything. Communication error and timeout The Danfoss controller is used for applications where temperature is critical. The key can contain up to 25 different sets. Time delay for cooling long alarm delay This time delay is used during start-up recovery timeduring defrost, in the cooling phase after a defrost.
Thermostat Set point Regulation is based on the set value plus a displacement, if applicable. Buttons and packing are imbedded in the front.
Controller for temperature control – EKC Manual |
The refrigeration and the fans are stopped. Push the upper or the lower button and select the new value 3. Off when DI is open.
When two compressors are cut in and out the two relays will operate in opposite directions. Push the uppermost or lowermost button to scan the rolling stack.
Defrost ekcc temperature The defrost is stopped at a given temperature which is measured with a sensor danfoxs sensor is defined in d If the Compressor in operation is unable to lower the temperature to the cutout point, the other compressor will danfosw cut in again.
If the settings in the controller are to be protected with an access code you can set a numerical value between 0 and Defrost can be accomplished with ekx or natural defrost. R22 Medium and high temperature scroll air-cooled condensing unit Open air outlet from side scroll ZB series.
The interval time is not active when set to 0. However the view of —d- will be discontinued if: Fitting the EKC controller with a plug-in module for communication gives access to all parameters of the controller. EKC B Controller with two relay outputs, extra temperature sensor and digital input.
Defrost start can also be accomplished via contact signals or manual start-up. The individual status codes have the following meanings: Delay on outputs during start-up Other displays: Push the middle button until the parameter value is shown 4. OFF-time in minutes Time delay for couplings of two compressors Settings indicate the time that has to elapse from the first relay cuts in and until the next relay has to cut in. Here you define which: Push the upper or the lower button and elc that parameter you want to change 3.
Access code 2 Access to adjustments There is access to adjustments of values, but not to configuration settings.